(888) 505 0828
Performing Residential & Commercial Property Inspections
Miami Dade, Broward, & Palm Beach
HOW THERMOGRAPHIC INSPECTIONS WORK
Thermography measures surface temperatures by using infrared video and still cameras. These tools see light that is in the heat spectrum. Images on the video or film record the temperature variations of the building's skin, ranging from white for warm regions to black for cooler areas. The resulting images help the inspector determine whether insulation is needed. They also serve as a quality control tool, to ensure that insulation has been installed correctly.
A thermographic inspection is either an interior or exterior inspection. The inspector decides which method would give the best results under certain weather conditions. Interior scans are more common, because warm air escaping from a building does not always move through the walls in a straight line. Heat loss detected in one area of the outside wall might originate at some other location on the inside of the wall. Also, it is harder to detect temperature differences on the outside surface of the building during windy weather. Because of this difficulty, interior surveys are generally more accurate because they benefit from reduced air movement.
Thermographic scans are also commonly used with blower door test running. The blower door helps exaggerate air leaking through defects in the building shell. Such air leaks appear as black streaks in the infrared camera's viewfinder.
Thermography uses specially designed infrared video or still cameras to make images (called thermograms) that show surface heat variations. This technology has a number of applications. Thermograms of electrical systems can detect abnormally hot electrical connections or components.
Thermograms of mechanical systems can detect the heat created by excessive friction. Inspectors use thermography as a tool to help detect heat losses and air leakage in building envelopes.
Infrared scanning allows inspectors to check the effectiveness of insulation in a building's construction. The resulting thermograms help inspectors determine whether a building needs insulation and where in the building it should go. Because wet insulation conducts heat faster than dry insulation, thermographic scans of roofs can often detect roof leaks.
In addition to using thermography during an energy assessment, you should have a scan done before purchasing a house; even new houses can have defects in their thermal envelopes. You may wish to include a clause in the contract requiring a thermographic scan of the house. A thermographic scan
performed by a certified technician is usually accurate enough to use as documentation in court proceedings.
TYPES OF THERMOGRAPHIC INSPECTION DEVICES
There are several types of infrared sensing devices used by on-site inspectors.
A spot radiometer (also called a point radiometer) is the simplest. It measures radiation one spot at a time, with a simple meter reading showing the temperature of a given spot. The inspector pans the area with the device and notes the differences in temperature.
A thermal line scanner shows radiant temperature viewed along a line. The thermogram shows the line scan superimposed over a picture of the panned area. This process shows temperature variations along the line.
Thermal imaging, the method that Fleet Inspections uses and the most accurate, utilizes a thermal imaging camera which produces a 2-dimensional thermal picture of an area showing heat or cooling leakage. Spot radiometers and thermal line scanners previously mentioned do not provide the necessary detail for a complete home energy assessment vs. thermal imaging.
PREPARING FOR A THERMOGRAPHIC INSPECTION
To prepare for an interior thermal scan, the homeowner should take steps to ensure an accurate result. This may include moving furniture away from exterior walls and removing drapes. The most accurate thermographic images usually occur when there is a large temperature difference (at least 20°F [14°C]) between inside and outside air temperatures. In northern states, thermographic scans are generally done in the winter. In southern states, however, scans are usually conducted during warm weather with the air conditioner on.
Some times of the year, because of a phenomenon known as “thermal loading,” it might be necessary for the homeowner–depending on local conditions--to create and maintain a specific inside/outside temperature difference for a period of up to four hours before the test will be performed. Running the air conditioner in cooling climates or the central heat in heating climates can do this.
Welcome! This form is the fastest method to start the booking process & schedule an inspection appointment ASAP with the insured / homeowner.
HAVE A QUESTION? GET THE FASTEST RESPONSE BY EMAILING US AT email@example.com